- Site Analysis
- Site Use
- Passive Design
- Material Use
- Space heating
- Lighting design
- Water heating
- Active ventilation
- Electrical design
- Renewable electricity generation
- Bioenergy and Biofuels
- Wet Areas
- Health and Safety
- Other Resources
Designing homes to conserve energy and use it efficiently, from sources that cause least environmental harm.
Heat pump configuration and installation
There are various configuration options for heat pumps.
On this page:
- Configuration options
- Outdoor unit
- Indoor unit
Air-to-air heat pump design options include:
- split – the outdoor unit supplies a separate indoor unit located in the space being heated or cooled
- multi-split – one outdoor unit supplies a number of indoor units
- ducted – one indoor unit located in a building void space (such as above the ceiling) has many supply ducts to a number of rooms, separately controlled by air flow rate.
Heat pumps may operate as:
- an inverter system – where a variable speed compressor motor maintains a constant temperature setting with small fluctuations
- a fixed speed system – where a single speed compressor in the outdoor unit operates at a constant speed and is either on or off.
Inverter systems are more commonly installed as they are approximately 30% more efficient than fixed speed systems. They achieve the set temperature more quickly than fixed speed systems, and the speed control gives a quieter operation.
Other features to consider include:
- demand defrost control – this will minimise the defrost cycle, reducing heat pump energy use and supplementary energy use
- programmable thermostat – allowing the home occupier to preset operating times, which reduces the temptation to oversize equipment to get rapid warming or cooling
- variable speed handler – providing better operational performance, particularly in hot climates.
Heat pump outdoor unit
To maximise heat transfer and heat pump capacity:
- the outdoor unit’s air inlet path needs to be unobstructed
- the outlet air needs to be directed away from the coil and the air inlet.
It is essential to have unimpeded air flow around the coil. Do not position the outdoor unit under the building or under decking.
The gap from the outdoor unit to any obstruction needs to be at least 500 mm on the air inlet and outlet faces, and 100 mm on any other face.
Consider the heat pump’s primary use when siting the outdoor unit. For best performance for heating, locate the outdoor unit in the warmest location, e.g. on a north or west facing wall (and vice versa for cooling). Heat pumps are most efficient when the temperature differential between outdoor and indoor temperatures is at its lowest.
The unit’s compressor and fans will create noise, so position the unit to minimise inconvenience to the occupants and to neighbours:
- Locate it away from quiet areas like bedrooms.
- Mount the heat pump chassis on neoprene isolation mounts or pads (to absorb any vibration).
- Avoid wall-mounted outside fans as these are likely to transmit vibrations.
- Maintain the unit regularly to ensure worn bearings and other parts do not become noisy.
- Use a fence or other barrier to block noise from neighbours – the most effective is a block mass in line of sight of the unit.
Particular care is required in retrospective installations, to ensure sound and vibration insulation is effective.
Locate the outside and inside units as close as practically possible, as excessive pipe runs limit output by reducing compressor cooling and can even cause compressor failure.
Heat pump indoor unit
The indoor unit heats/cools, dries and circulates the room air and normally contains a coil, fan, air filter, air vanes and condensate pipe. The indoor unit can be:
- wall or high wall – mounted high on the wall, this brings air in from above and directs air downwards
- under ceiling – mounted on the underside of the ceiling, near to a wall, this brings air in from below or the wall side and directs air across the room at ceiling level
- ceiling cassette – mounted within the ceiling panels, this brings air in from below at its centre and directs air out from each of the four edges at ceiling level
- floor – mounted on or just above the floor and against a wall, this brings air in from below or from floor level and directs air up the wall.
For air to freely circulate, there should be no obstruction around the unit. The best location for a reverse cycle heat pump is near ceiling level. The best location for a heating-only heat pump is at floor level. (Note that these units are not interchangeable – those designed for use high on a wall should not be used close to floor level.) For a ducted system, the best location is in the ceiling space, with the supply and return air ducts located as far apart as possible.
Effective air flow is important:
- If mounted too close to the ceiling, a unit may short cycle and shut down prematurely.
- If the unit is located in a corner, the room may be only partially heated or cooled.
- If the location is subject to draughts, the unit’s performance may be affected.
Update: 17 June 2013